problem 1air is at dry bulb temperature of 34 c and rh1 of 55 is being
Problem 1Air is at dry bulb temperature, of 34° C and RH1 of 55%, is being cooled in a Cooling and Dehumidification coil, the air leaves the coil at temperature, 16° C. Air is used to cool lumber of size12 m at a drying rate of 8kg/hr. 1. (4pt) Obtain the most accurate values for the following parameters using the attached Psychometric chart: (Show your work clearly on the attached chart!)
) Calculate the volume flow rate (dry air), required by the process Calculate the required amount of kW by the process t) Calculate the amount of heat transfer due to sensible cooling phase only
*The amount will be in form of wallet points that you can redeem to pay upto 10% of the price for any assignment. **Use of solution provided by us for unfair practice like cheating will result in action from our end which may include permanent termination of the defaulter’s account.Disclaimer:The website contains certain images which are not owned by the company/ website. Such images are used for indicative purposes only and is a third-party content. All credits go to its rightful owner including its copyright owner. It is also clarified that the use of any photograph on the website including the use of any photograph of any educational institute/ university is not intended to suggest any association, relationship, or sponsorship whatsoever between the company and the said educational institute/ university. Any such use is for representative purposes only and all intellectual property rights belong to the respective owners.